When your computer system can't be without power evenfor maintenance - a Liebert MicroPOD ensures continuous uptime. The MicroPOD provides maintenance bypass capability as well as power output distribution, and can be used with virtually any micro-UPS system. The MicroPOD allows you to manually transfer your connected equipment to utility power via a maintenance bypass switch, permitting scheduled maintenance or UPS replacement without power disruption. Transferring back to UPS power is just as easy - just turn the switch to the indicated position and your load isprotected by the UPS.
|Power Rating||3 kVA|
|Temperature||-4F (-20C) to 140F (60C) Storage|
|Humidity||0 to 95% Non-condensing Relative Humidity Storage|
|Frequency Band||The POD is designed to operate as a maintenance bypass system in the following modesNormal - The UPS is continuously supplied available utility power by the POD. The UPS output power is returned to the POD and distributed to the critical AC load through the POD output receptaclesMaintenance Bypass - The bypass switch allows a transfer of the critical AC load from the UPS inverter to the utility source; to allow for service to or replacement of the UPS, without interrupting the loadBypass Switch: The bypass switch is capable of switching up to 20 or 30 amps, based on the model of the POD. The switch is a break before make type, with a maximum transfer time of 6msConnection to UPS Input: 5-20RConnection to UPS Output & cord length: 5-20P on attached 6 foot cord|
|Output Receptacles||8 x NEMA 5-20R|
|Circuit Breaker||Two 20A Fuse|
|Current||16 A Output Current|
|Output Voltage||120 V AC|
|Input Receptacles||NEMA 5-20P|
When your computer system can't be without power evenfor maintenance - a...
Maintenance-free Lead Acid Hot-swappable
Hot Swap BatteriesPlug-and-Play installation
Liebert MPH is a flexible rack power distribution unit (PDU); a perfect...
Generac 6297 - Switched Neutral Kit For Generac/Gen-Tran Manual Transfer...